In addition to the standard booth design conduits and boxes, booth building units will have empty 2″ x 4″ J-Boxe(s) mounted under the shelf with 1/2″ empty conduit runs and a pull string to the stub area for data and communication lines by others.
This design provides an easy pathway for typical items added to customized guardhouses on site.
The standard booth design for the electrical system will have all U.L. approved fixtures wired to N.E.C. standards. Units shall have interior LED light(s) recessed in a 16 gauge galvanized steel ceiling painted to match the booth interior color and controlled by a single-pole wall switch, dimmer switch, or occupancy sensor. The unit will also have a 20 amp duplex outlet receptacle mounted under the shelf.
All items will be wired to 125 Amp rated, 120/240 volt, 12 pole, 3 wire single phase load center.